Join Date: Jul 2008
Location: Smithfield, RI
Thanked 0 Times in 0 Posts
Rep Power: 7
Even if someone goes and switched all the bulbs from LED to halogen, max possible load will probably never even approach 30A. I was thinking I should swap the main breaker in the panel from 50A down to 30A, because I don't want the wire to be too small for the breaker if i size for 30A.
But then you mentioned a fuse in the positive feed wire. So if I fuse the feed at 30A right near the positive battery terminal (on just the house battery) then I guess that issue is resolved.
But in that case, why do I have a 50A breaker on the panel?
Scampi 30 MK-IV
To view links or images in signatures your post count must be 10 or greater. You currently have 0 posts.