Join Date: Feb 2005
Thanked 0 Times in 0 Posts
Rep Power: 0
ok - my Perko switch did have a terminal 1, terminal 2 and common. Hooked everything up per cap'n dave and it seemed to go pretty well, Except..............
I have a wire that leads off to an electrical panel. Basically a panel to cut on and off various house items. Running lights, cabin lights, etc. My assumption is that his terminal should go on the same switch terminal as teh house battery. Would this be correct?