Join Date: Feb 2011
Location: San Francisco Bay area
Thanked 70 Times in 70 Posts
Rep Power: 6
Re: Electrical propane shut off valve
You can go from the tanks to a T with the output going next through the regulator. From the reg another T and a solenoid on each line.
I have not seen a dual solenoid installation on any boat.
Most installations I have seen use one solenoid and regulator with a T to the appliances similar to that shown below.
Just wanted to mention that the code now, for a two tank installation, is to have a regulator with two gauges, and two hose connections, so that each tank can be individually leak checked. I have a PR
-5412 (scroll down).
All your comments about the second T arrangement I agree with though.
Marine Propane System Products from Fireboy-Xintex
I also have the S1-A leak detector and solenoid valve control.
Bristol 31.1, San Francisco Bay