Join Date: Nov 2009
Thanked 100 Times in 92 Posts
Rep Power: 7
Re: Power Outlet Sizzle - Help Please
No, you should not simply buy new units, plug them in, and be on your way.
You have no idea what caused the failure, and could cause a fire and lose your boat next time.
Either you overloaded the circuit, or you suffered a short circuit.
If you have suffered a ground fault, and had GFCI outlets installed as the surveyor recommended, the outlet would have tripped, saving you from damage.
It's impossible to know for sure what went wrong based on the limited information you've provided. Find an electrician and get it fixed right. Not only will you save your own boat from burning, but perhaps your neighbors' boats as well.
I just noticed that you were running the space heater and the iron. Most likely (but not definitely), you have overloaded the outlet and melted down the guts of the outlet, or perhaps the wire in the run somewhere.
I suspect this was a 15 amp circuit, and the iron and space heater took you up to 14.9 amps. Not enough to trip the breaker for an overload, but enough to "boil the frog", and melt down the wiring.
For future reference, do not continuously load a 15 amp circuit more than 80% of it's rating.
15 * .8= 12 amps. Don't continuously draw more than 12 amps on any single 15 amp circuit. That's for the whole string of outlets on that 15 amp breaker, not 15 amps per outlet.
S/V Old Shoes
1973 Pearson 30 #255
Last edited by Ajax_MD; 02-01-2013 at 11:49 AM.